Can’t see the big picture, but it looks like they are installed properly. You say there was a problem with main2. Of the remaining circuits, the dryer probably is zero as main1 would be greater than 226 Watts if it were on. The stove would probably do the same if it were on, and I would expect power factor greater than .92 if the dryer or stove were on.
That leaves the Woodshop_2 circuit. Why do you believe it should be non-zero? Can you move that CT to the same conductor along side Woodshop_1 and see if it reads differently? Same with Main_2 and Main_1 if you feel Main_2 should not be zero.
Another test might be to start the dryer and take a screenshot of the status display with it on to see what the Mains read as well.