Finally installed my unit after waiting 3 wks USPS delays! The daily energy consumption matches nbrs from my electric supplier for last 3 dys, so thats good news. Problem is, whenever my clothes dryer (240V red/black wires) comes on, the TOTMisc watts go up dramatically. The dryer is connected to a separate 100A subpanel and I have 2 CTs connected to it. Looking at the last photo, when dryer is ON, you can see that TOTMisc goes from 124.1W to 806.6W. And when Off, it goes back down to 120+W. Am I missing something here or is there something amiss with my circuits? Could the SCT013 CTs be defective and way off in its measurements?
Comparison of Dryer Off and On: